Manuals for buderus juno c to download for viewing them online or printout as PDF. Manuals for Buderus Juno 11 download to download for viewing them online or printout as PDF. Buderus Manuals for Support Juno /SF Buderus | GB | Operating instructions | Buderus GB Operating instructions . .. 46 Shut down the heating system using the control unit.
|Published (Last):||16 August 2010|
|PDF File Size:||8.20 Mb|
|ePub File Size:||7.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
It is not essential for the boiler to be positioned this way; As long as the joists are capable of supporting the flue via the support plate supplied in the kit.
The heating circuit operates in automatic mode. Open main shut off valve. Check that there is oil in the tank and that the supply valve is open.
It should be complete with the following: Hold “Day mode” down, and turn the rotary selector until the required number of hours is displayed here: Check whether the limit light on the control fascia is glowing, if so it indicates an overheat situation. buserus
All models are bueerus for connection to a conventional chimney or any of the available Camray 5 Combi Balanced Flue options. Check the burner, the heat exchanger and the condensate trap for pollution.
Buderus GB Operating instructions |
To increase the height additional or mm extensions can be added up to the maximum number indicated. Drill 6 holes to secure sections to adjacent ones and secure with the self tapping screws supplied. Allow system to cool, check pressure in system and Air trapped in boiler heat repressurise if required.
For high level vertical or conventional flue remove and discard the top blanking plate, replacing the plastic studs in the fixing holes. Ensure that the Burner Oil Pump is correctly set for two Pipe operation. The sensor should be located above the Burner in the clip provided, see figs.
Typengeprüfte Gebläsebrenner, Heizkessel und Wassererwärmer
Research has bhderus that it is generally sufficient to run the DHW circulation pump for only three minutes every half hour. Improper installation, adjustment, alteration, service buderys maintenance can cause injury, loss of life or property damage.
I Instantaneous water heater. Subject to the modules, various of the following operating displays can be called up: This allows the condensate to drain away. Relief muno The indirect DHW tank must have a temperature and pressure relief valve installed.
Pressure Relief Valve This should be checked for operation during annual servicing by increasing the system pressure outlined in Section 7: Midday program Monday at If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury or death.
Operating instructions Logamatic 4211
Under the cover a RC system controller can be installed not available. The burner servomotor cannot be reversed. Suitable for new installations and for replacing existing sealed system Boilers.
These figures may be used to calculate combustion efficiency. Low Level Horizontal 2. Installation and service must be performed by a qualified installer, service agency or the gas supplier.
In emergency mode, all pumps continue to run and the mixers are volt-free. FM — heating circuit 3, heating circuit 4 Logamatic – Subject to technical modifications. Create sided timber framed box for the Support Plate S. Partially scaled up plate heat exchanger blockage on incoming mains to boiler Fault on cold mains supply to residence.
Joints in the Flue Pipe must not be situated within the joist space.